This could work, but you will want to run an extra bond from the panel to the metal siding (as an extra precaution)--using a clamp or such as your fastening for the bonding jumper. Make sure the wire is close to the panel. You could also run a clamp from your siding to the supplimential grounding conductor being ran to your ground rods. The wire coming the panel to the rods must not be broken (cut) to accomplish this. Wait for others to comment.
If you can securely bolt your panel to the building structural metal, then that could bond it.
Last edited by Ohm1; March 6th, 2006 at 11:50 PM.
Learning brings success. While you are waiting, I'm getting better!