Open neutral in receptacle
Thanks for your reply! I used a plug-in tester (with the 3 light indicator) to determine the open neutral condition. I will check the voltage as you suggested later in the week. The receptacle itself is wired correctly with the black wire to brass & white to silver.
I had already checked the connections in all switches and receptacles in the bathroom on the circuit and found no apparent problems. Perhaps there is another receptacle feeding this one. Any suggestions as to how to find it quickly & easily?