ive been reading over the forums and google for my problem. It seems alot have it. so heres the deal
50 amp double pull at the panel - 240v
60 amp gfci breaker
Hot tub input
Everything is correct on the gfci -- netural load goes to the breaker and the pigtail then goes to the netural bar that the panel side comes into.
its clearly labled in the hot tub where to put what. when i have the transformer that takes 120v down to 12 and 24v and 5v the gfci doesn't trip instantly. but if i have that connected it instantly trips.
So being the somewhat genious i am not i decided to just buy a new transformer thinking that was the issue ( was ohming out the transformer to get a +1.03 between ground and the 120.)
I instaled the new one i just got in the mail. and low and behold problem is still there.
so i just pulled the board and inspected everything .. nothing seems burnt or corroded and the 120v black goes to a fuse that then transfers power to the 3rd pin of the 7 pin connector to this transformer. i have 120v on this pin ( verified ) but can't troubleshoot past this point with no power.
(ps) i have unplugged everything from this board and as long as that transformer is plugged in it instantly trips.